Category: ODF & SAE CONNECTIONS
Surface treatments applicable: no
100% GUARANTEED RELIABILITY AND SAFETY the opening and closing operations are always sealed
100% TESTED using a dedicated helium plant 100% TRACEABLE by serial number and batch date which certify the passing of the test
The liquid receiver valve series 43100 is designed to withstand 1.43 times the PS according to the standards set by the Directive 2014/68 / UE. In addition, laboratory tests certify the resistance of the tap to bursting pressure equal to 3xPS according to the provisions of EN 378-2: 2016.
The receiver valves in the series 43100 are designed to be installed on refrigeration and air-conditioning system for
domestic and industrial use. It’s possible to use them with all the refrigerant fluids of group 2 of Art.13, Chapter 1,
point B, of European Directive 2014/68/EU, with reference to EC Regulation no. 1272/2008.
Below i s a list of the main refrigerant gases that can be used:
HFO/HFC blends, HC
The main construction components of the receiver valves in the 43100 series are:
Make sure the refrigeration/conditioning system is properly clean before installing the valve with a 2/2way screw plug. The presence of impurities could affect the sealing of the valve. Valve opening/closing is very easy: you only need to remove the protection cover and rotate the pin clockwise to close the valve and anti-clockwise to open it, using an Allen wrench. Then remount the protection cover.